How to deal with sudden short circuit of diesel generator set?
Characteristics of sudden short circuit
1. In steady state short circuit, the synchronous reactance is large. Therefore, its steady-state short-circuit current is not large. However, when the short circuit occurs suddenly, the transient reactance limiting the current is very small. And it contains DC component, so the sudden short-circuit current is very large. Its peak value can reach more than ten times of the rated current.
500kw 625kva diesel generator price for sale产品在售
2. With the appearance of this impulse current. The winding of the motor will be subjected to a great impact electromagnetic force. It may deform the winding and even damage the insulation of the winding.
3. In the process of sudden short circuit. The motor is affected by strong short-circuit torque. Vibration may occur.
4. The stator and rotor windings of the motor have overvoltage.
Characteristics of internal physical phenomena of generator under sudden short circuit
The armature current is constant during steady state short circuit. The corresponding armature magnetomotive force is a constant amplitude rotating magnetic field rotating at synchronous speed. As a result, no electromotive force is induced in the rotor winding and current is generated. From the current relationship, it is equivalent to the open circuit state of the transformer.
In case of sudden short circuit, the magnitude of armature current varies. The amplitude of the corresponding armature magnetic field is variable. Therefore, the transformer acts between the stator and the rotor. The induction potential and current in the rotor winding will affect the current change in the stator winding. From the electromagnetic relationship, it is equivalent to the sudden short circuit state of the transformer.
300kw 400kva water cooled diesel engine price产品在售